STANDARD METHOD OF FIRE TESTS OF FIRESTOP SYSTEMS
1.1 This method of test is applicable to firestop systems with or without penetrating items such as cables,
cable trays, conduits, ducts and pipes. These firestop systems are intended for use in openings in fire
resistive wall and floor assemblies and membranes forming part of an assembly required to have a fire
resistance rating and linear openings between adjacent fire resistive floor assemblies, wall assemblies or
1.2 Tests conducted in conformance with this method will record firestop performance during the fire-test
exposure under laboratory conditions; but such tests shall not be construed as determining suitability of
the firestop system for use after exposure to fire.
1.3 The test method allows for the testing of the resistance of firestop systems to an external force
simulated by a hose stream. However, this method shall not be construed as determining the performance
of the firestop systems during actual fire conditions when subjected to forces such as failure of cable
support systems and falling debris.
1.4 Provisions are included to allow for testing with a pressure differential between the furnace chamber
and the exterior.
1.5 It is the intent that tests made in conformity with these test methods will develop data to enable
regulatory bodies to determine the suitability of firestop systems for use in assemblies where fire
resistance of a specified duration is required.
1.6 Provisions are included to allow for optional air leakage testing to determine the air leakage rate
through test specimens resulting from a specified air pressure difference applied across the surface of the
test specimens. The results of this test are intended to develop data to assist in determining the
acceptability of firestop systems with reference to the control of air movement.
NOTE: Tests for air leakage are performed under laboratory conditions. In actual usage, results may vary because of
installation and/or environmental conditions. See Appendix A, Subsection A6.
1.7 For the purpose of this Standard, a firestop system (fire stop) refers to a specific construction
A Any device intended to close off an opening or penetration during a fire;
B Material(s) that fill an opening in a wall or floor assembly where penetration is by cables, cable
trays, conduits, ducts and pipes along with their means of support through the wall or floor
C Material(s) that fill an opening in a wall assembly where penetration is by electrical and nonelectrical
outlet boxes along with their means of support in the wall assembly;
NOTE: Examples of non-electrical outlet boxes are for the supply and waste water to/from
washing machines, the air exhaust from dryers, gas outlet boxes, or other devices that create
an opening in the assembly.
D Material(s) and construction intended for use in linear openings between adjacent fire resistive
1.8 This test method is also applicable to perimeter joint firestop systems located between a fire
resistance rated floor and a rated or non-fire resistance rated exterior wall.